Marmitek X10 DIN Rail Dimmer LD11
- Installs at the breaker panel/fuse box for X10 control of branch lighting circuits rated up to 700W.
- Controlled via X10 controllers or momentary action wall switches, including "designer" wall switches.
- Designed to operate with 230V lighting including mains halogen.
- Remembers its light level for smooth dimming.
The Marmitek DIN rail dimmer is a 700W receiver unit that works as a remote dimmer. Mounted on the "Top Hat" DIN rail in the mains distribution box, it dims or switches hardwired circuits with several wall switches (eg. Living room lighting). It is designed to operate with 230V lighting including mains halogen.
The unit can be turned on/off, and brightened/dimmed either by an X10 controller or by external momentary action switches connected to Terminal 2. It responds to "standard" X10 commands. ie. All-Lights-On, All-Units-Off, On, Off, Bright and Dim. It also responds to extended X10 commands. Combined with the memory dim feature, the LD11 can change the room lighting instantly or progressively. This unit is especially designed for scene lighting where very often the lighting is mains powered 12V halogen, commonly used in living room, study/reading rooms. The unit can be installed in sub-junction boxes for discrete control.
This Marmitek unit can control branch lighting under X10 control or, if momentary switches are installed, with designer style wall switches.
Dimensions: Length 50, Width 80, Height 65 mm.
Supply voltage: 230V +10%/-15% 50Hz
Supply current: =< 20mA capacitive
Making capacity: 60W to 700W (incandescent lamps only). Maximum 300W of 12V Low voltage lighting with suitable transformer.
Regulating time: 3.5s +- 0.2s from full On to Off
EMC emission: According to EN50081-1
EMC immunity: According to EN50082-1
Electrical safety: According to EN60950 and EN60065
Signal sensitivity: 15mVpp min 50mVpp max at 120KHz
Input impedance: => 60 Ohms (L-N) at 120KHz
Connections: Screw type terminals for phase, neutral,
switched phase, control 2
Ambient temperature: -10C to +50C (operation); -20C to +70C (storage)
This product is CE approved for use in the EU.
How to Install
SWITCH OFF APPROPRIATE MAINS FUSE AND MASTER SWITCH! (INSTALLATION BY A CERTIFIED INSTALLER)
1. Mount the LD11 using the schematics below.
2. Set the rotary code switches on the front side to the desired address.
When mounting more LD11 dimmers next to each other, depending on the load per LD11, keep an extra distance of 2 cm between each LD11 to ensure the heat dissipation. With the help of additional momentary switches on input 2, the module can be switched on or off by a short key press and can be dimmed by a long key press.