Marmitek X10 DIN Rail Switch
We currently have a limited stock of AD10 and AD11 DIN Rail modules, but are looking to re-manufacture these shortly. If we're out of stock, please add your e-mail address to the box above and click 'Notify Me' to be alerted when we have re-stocked these.
- Install at the circuit breaker/fuse box for X10 control of branch lighting circuits or appliances rated up to 16A (ideal for air conditioning, heaters, etc).
- Works with an X10 controller and standard latched or momentary action wall switches, including "designer" wall switches.
The DIN rail switch is an X10 controlled relay. Discreetly installed at the distribution box, it switches hard-wired circuits with several switches (e.g. hallway lighting). The internal relay can be tripped either by external latched or momentary action standard wall switches or by an X10 controller. It responds to "standard" X10 commands (All-Unit-Off, On and Off). When the relay is energised, the LED above the slide switch is illuminated.
Terminal 1 is designed for toggle switches: the relay picks up when phase is present and releases when there is no voltage at the terminal.
Terminal 2 is designed for pulse contacts: each time phase is applied the relay switches from one state to the other.
This unit can replace any pulse contact relay that is commonly used for multi-switched hall and entry lighting. In discrete locations, e.g. kitchen lighting, you may prefer to install the AD10 in a small sub-junction box.
Length 88mm, Width 35mm, Height 65mm.
Supply voltage: 230V +10%/-15% 50Hz
Supply current: =< 20mA capacitive
Making capacity: 2000W for light bulbs and halogen lighting (incandescent lamp), 700W for inductive/capacitive load (motors), 3600W for resistive (ohm) load
EMC emission: According to EN50081-1
EMC immunity: According to EN50082-1
Electrical safety: According to EN60950 and EN60065
This product is CE approved for use in the EU.
Signal sensitivity: 15mVpp min 50mVpp max at 120KHz
Input impedance: => 180Ohms (L-N) at 120KHz
Connections: Screw type terminals for phase, neutral, switched phase, control 1 and 2
Ambient temperature: -10ºC to +40ºC (operation); -20ºC to +70ºC (storage)
How to Install
SWITCH OFF APPROPRIATE MAINS FUSE AND MASTER SWITCH! (INSTALLATION BY A CERTIFIED INSTALLER)
1. Mount the AD10 using the schematics below.
2. Set the rotary code switches on the front side to the desired address.
Description of the selector switch
Position 0: The connected load is switched off and cannot be switched on using one of the wall switches or Marmitek X-10 Commands.
Position 1: The connected load is switched on and cannot be switched off using one of the wall switches or Marmitek X-10 Commands.
Position Auto: The connected load can be switched on or off using one of the wall switches or Marmitek X-10 Commands.
Terminal 1 of the switch is designed for toggle switches: the relay picks up when phase is present and releases when there is no voltage at the terminal.
Terminal 2 of the switch is designed for pulse contacts. Each time phase is applied, the relay switches (i.e. from OFF to ON or vice versa).